SKU: PD6603-LNN Product Type: 1/8 DIN Loop-Powered Digital Panel Meter Input: Current (4-20 mA) Output Options: (2) Open Collectors Approvals: CE Display: Dual Line, 0.7″ & 0.4″ High, F & I and 8 Digits, LCD Warranty: 3 years Backlight: Standard / Red on Alarm Product Series: Loop Leader Product Family: PD6600
These loop-powered 1/8 DIN digital panel meters can be installed virtually anywhere to provide convenient and informative displays of any 4-20 mA signal. One of the most convenient features of these instruments is their dual line display which is typically used to display the process variable on the 5-digit alphanumeric top line and the units or a tag on the 8-digit alphanumeric bottom line. Another common setup is to display the input in one scale on the top line (such as feet) and another scale on the bottom line (such as gallons). Both of these lines use 14-segment, alphanumeric characters for clear indication of tags, units or alarm messages.
Further enhancing the display on these instruments is a 20-segment bargraph available on the PD6604 that also includes a numeric value of the percentage the bargraph represents.
There is even a model that displays level in feet and inches for customers who prefer to see their levels represented that way rather than in decimal format.
These loop-powered meters can be installed virtually anywhere because they get their power from the 4-20 mA loop and therefore require no separate power source. And they only drop 1.5 V (4.7 V with backlight), so they add very little burden to the loop. Additional features that allow these instruments to be installed virtually anywhere include a NEMA 4X, IP65 front panel, an operating temperature range of -40 to 167°F (-40 to 75°C) (for safe area products), conformally coated PCBs, and a backlit LCD that can be read in bright sunlight or dimly lit areas. Finally, there are intrinsically safe and nonincendive versions of these instruments that can be installed in hazardous areas.
Free, PC-based, software that connects to the meter via a micro USB cable is available for programming and setup of the meters. In addition, the meter can be programmed, setup and operated via the four front panel buttons. Three of these buttons can be used as function keys. In addition, a digital input is standard and is particularly useful for remote reset of the alarms or to trigger an alarm.
All models come equipped with two open collector outputs and are available with two solid state relays and 4-20 mA analog output options. The open collector outputs are useful for alarm indication or pulse output. The relays can be programmed for alarm indication, on/off control, or pump alternation.
Except where noted all specifications apply to operation at +25°C.
Input: 4-20 mA Accuracy: ±0.02% of span ±1 count, Square root and programmable exponent: 10-100% FS Voltage Drop:Without Backlight: 1.5 V maximum, With backlight: 4.7 V maximum Equivalent Resistance:With backlight off: 75 Ω @ 20 mA With backlight on: 225 Ω @ 20 mA Input Overload: Over current protection to 1 A maximum Temperature Drift: 25 PPM/°C from -40 to 75°C ambient Function: PV1: Linear, square root, or programmable exponent PV2: Linear or Round Horizontal Tank Low-Flow Cutoff: 0.0 to 999,999.9 HART Transparency: Analog input will not interfere with existing HART communications on the wired 4-20 mA signal
Display: Dual-line LCD with backlight. Both lines 14-segment alphanumeric. Top: 0.7″ (17.8 mm), Bottom: 0.4″ (10.2 mm). Display may be programmed to turn red and flash a user-defined message on alarm condition. Backlight: Powered by 4-20 mA loop. Intensity varies with signal level PD6602 & PD6606: Top line: 5 digits (-9999 to 99999) or 5 characters (all capital & most lower case letters) Bottom line: 8 digits (-9,999,999 to 99,999,999; separated by commas) or 8 characters (all capital & most lower case letters) Bargraph: None PD6603 & PD6607: Top line: -99FT 11IN 15/16 to 999FT 11IN 15/16 Bottom line: 8 digits (-9,999,999 to 99,999,999; separated by commas) or 8 characters (all capital & most lower case letters) Bargraph: 20 segments, numeric percent indication at top PD6604 & PD6608: Top line: 5 digits (-9999 to 99999) or 5 characters (all capital & most lower case letters) Bottom line: 8 digits (-9,999,999 to 99,999,999; separated by commas) or 8 characters (all capital & most lower case letters) Bargraph: 20 segments, numeric percent indication at top Decimal Point & Commas: Top line: Up to four decimal places Bottom line: Up to seven decimal places and commas to indicate 1000s (ie 88,987,628) Dual-Scale Feature: The input can be displayed in different scales on the top and bottom lines. For instance, the top line could display the input in height and the bottom line could display that same input in volume. Alarm Indication: Red backlight, flashing display, alarm symbol (!). Symbols are not available on bargraph models. Alarm Message: On or Off; user programmable, 8 characters maximum. Displayed every 10 seconds for 1 second on bottom line. Display Update Rate: Ambient > -10°C: 1 update/second Ambient -20 C: 1 update/2 seconds From -20°C to -40°C the update rate slows down 1 second for every -2°C (e.g. at -24°C, 1 update/4 seconds). Overrange: Top: 99999; Bottom: 99,999,999 (flashing) Underrange: Top: -9999; Bottom: -9,999,999 (flashing)
Environmental:Operating temperature range: -40 to 75°C for safe area products -40 to 70°C for hazardous area products Storage temperature range: -40 to 85°C Relative humidity: 0 to 90% non-condensing. Printed circuit boards are conformally coated. Programming Method: Front panel & Free PC-based USB programming software Enclosure & Materials: Enclosure: 1/8 DIN, IP65, NEMA 4X front panel, high impact plastic, NORYL® polyphenylene ether & polystyrene blend (PPE PS) resin, UL 94V-0, Color: gray, Gasket: silicone rubber, Faceplate: LEXAN® polycarbonate (PC) film, Buttons: silicone rubber Noise Filter: Averages the input signal over a period of time between 1 and 16 seconds to dampen the effects of a noisy signal that causes a jumpy display. Recalibration: Recalibration is recommended at least every 12 months. Max/Min Display: Max/min readings reached by the process are stored until reset by the user or until power to the meter is turned off. Tare: Zeros out display Password: Programmable password restricts modification of programmed settings. Non-Volatile Memory: All programmed settings are stored in nonvolatile memory for a minimum of ten years if power is lost. Normal Mode Rejection: 64 dB at 50/60 Hz Connections: Removable screw terminals accept 12 to 22 AWG wire. DI Digital Input Contacts: 2.1 VDC on contact. Connect normally open contacts across DI+ and DI DI Digital Input Logic Levels: Logic High: 2.4 to 30 VDC (max) Logic Low: 0 to 0.9 VDC Tightening Torque: Screw terminal connectors: 4.5 lb-in (0.5 Nm) Mounting screws: 8.0 lb-in max. (0.9 Nm) Overall Dimensions: 4.68″x 2.45″x 3.79″ (119 mm x 62 mm x 96 mm) (W x H x D) Weight: 8.7 oz (247g) with option board Warranty: 3 years parts and labor
Common Open Collector & Relay (Alarm) Specifications
High or Low Alarm: User programmable for high or low alarm Alarm Deadband: 0-100% FS, user programmable On & Off Time Delay: 0 to 9,999 seconds Fail-Safe Operation: Independent for each open collector and relay Alarm Operation: Automatic, Automatic with manual override, Latching (manual reset anytime), Latching with reset after cleared (manual reset only after alarm has cleared) Alarm Indication: Red backlight, flashing display, alarm symbol (!); (symbols not available on bargraph models) Alarm Message: On or Off; User programmable, 8 characters maximum. Displayed every 10 seconds for 1 second on bottom line Alarm Acknowledge: Front panel ACK button or external digital input resets output and screen indication Auto Initialization: When power is applied to the meter, open collectors and relays will reflect the state of the input to the meter Timer Output: One-shot or Continuous Off Time Delay: 1 sec to 99:59:59 (hrs:min:sec) On Time: 1 sec to 99:59:59 (hrs:min:sec) Stopwatch: Output turns on when started and off when stopped
Open Collector Outputs
Rating: Two NPN, Isolated open collector, 30 VDC @ 150 mA max Output Assignment: Pulse, Alarm, Timer, Stopwatch on/off, or Disable Pulse Output Source: PV (PV1, PV2) or Test Frequency Pulse Output Factor: 0.000001 to 999,999.9 Pulse Width: 0.5 ms @ 1 kHz; 500 ms @ 1 Hz; 50% duty cycle Pulse Output Frequency: 1,000 Hz maximum Quadrature Pulse Output: Available for Output 2 (90° behind Output 1) Alarm Output Source: Assign to PV (PV1, PV2) or Digital Input
Solid State Relays
Rating:Resistive Load: 250 VAC/DC @ 1 A Inductive Load: 75 VA @ 0.6 A, 250 VAC/DC max (Safe Area only) Noise Suppression: Metal oxide varistors across outputs Relay Assignment: Pump Alternation, Alarm, Timer, Stopwatch on/off, or Disable Alarm Output Source: Assign to PV (PV1, PV2) or Digital Input Pump Alternation: Relays will alternate with each pump cycle and alternation can be based on elapsed time. Pump alternation time can be programed for: 0 to 999:59 (hrs:min) Relay (Pump) Runtime: Meter will keep track of how long each relay (pump) has operated and display this information Relay (Pump) Cycles: Meter will keep track of how many times the relays (pumps) have cycled and display this information
4-20 mA Transmitter Output
Accuracy: ±0.05% FS ±0.001mA Output Source: PV1, PV2, re-transmit; reverse scaling allowed Scaling Range: 1.00 to 23.0 mA Disable: High impedance state, less than 1 mA Calibration: Factory calibrated 4.00 to 20.00 mA Underrange: 1.0 mA, 3.5 mA, or 3.8 mA (If input < 3.5 mA), or Off; user selectable Overrange: 20.5 mA, 20.8 mA, or 23.0 mA (If input > 20.5 mA), or Off; user selectable Isolation: 500 V input-to-output Temperature Drift: 0.5 μA/°C max from -40 to 75°C ambient External Loop Power Supply: 7.0 VDC to 30.0 VDC maximum Output Loop Resistance: 10-750 Ω @ 24 VDC; 100-1100 Ω @ 30 VDC
Signal Input Conditioning
Non-linear input signals (i.e. weirs & flumes, differential pressure, etc.) can be linearized with the ProVu’s simple to use built-in signal input conditioners, such as square-root extractor, exponential linearizer, horizontal round tank linearizer, or the ProVu’s powerful general purpose 32-point linearizer.
Weir Flow Calculated Using Exponential Math Function
Round Horizontal Tank Math Function
For pump control applications where 2 or more similar pumps are used to control the level of a tank or a well, it is desirable to have the pumps operate alternately; this prevents excessive wear and overheating of one pump over the lack of use of the others. The ProVu can accommodate up to 8 pumps. In the example below, a pair of relays have been set up to alternate every time an on/off pump cycle is completed. Another pair of relays is used for low and high alarms.
Free Meterview XL PC-Based Programming Software
The main screen displays an image of the connected meter and includes various information about this meter, such as model number, readings, and status.
Free, PC-based, MeterView XL software that connects to the meter via a micro USB cable is available for programming and setup of the meters. This software greatly simplifies the programming process and also allows the user to save configuration files for later use. The meter will also be powered by the USB connection so no additional power is needed during programming.
Easiest Way to Program Your Loop Leader
Convenient USB Connection
Meter Powered by USB Connection During Programming
Save & Print Configuration Files without Meter Connected
Panel cutout required: 1.772″ x 3.622″ (45mm x 92mm)
Panel thickness: 0.040 – 0.250″ (1.0mm – 6.4mm)
Mounting brackets lock in place for easy mounting
Clearance: Allow 6″ (152 mm) behind the panel
Loop Leaders, when ordered with the two solid state relays, have several features that make them ideal for simple duplex pump control. The relays can be programmed to alternate the pumps based on level and runtime thus ensuring even wear on both pumps. If the level remains constant (within on/off points), alternation is based on runtime. If the level cycles the on/off points, alternation is based on level and runtime. If the run time is set to 0, alternation is based on level. The meter also keeps track of runtime for both pumps and the number of times they have cycled.
In addition to the two solid state relays for controlling pumps, the Loop Leaders two open collectors could be used to indicate high or low level alarm conditions.
The Loop Leader can be used as a pump controller to alternate two pumps and provide high and low level alarm indication. The pumps can be programmed to alternate on level and run time and the meter can display the pump run times and the number of times they have cycled. The PD6606–L2N can be used as an intrinsically safe pump controller.
Signal Input Conditioning
The PD6600 Loop Leader process meter allows you to select the signal input conditioner applied to the input: linear, square root, programmable exponent, or round horizontal tank volume calculation.
The programmable exponent function is used to linearize the level signal in open channel flow applications using weirs and flumes and display flow rate in engineering units.
The square root function can be used to linearize the signal from a differential pressure transmitter and display flow rate in engineering units.
The round horizontal tank linearization function automatically calculates the volume in a round horizontal tank with flat ends.
A digital input comes standard on the Loop Leader PD6600 Series. This allows the user to program an external button to activate certain functions immediately like alarm acknowledgement, display minimum/maximum values, tare the display, reset a value, and many more. This allows the Loop Leader to be greatly customized for use in specialized applications. See the PD6600 series manuals for all digital input functions.
Application Timers are used in everyday life; one of the most common examples is the microwave oven. Industrial timers are used in process control applications where certain events or actions need to be controlled by time. Examples include automatic and batch control applications, where the relay needs to be energized for a specific length of time.
The timer fuction is available on the open collector and relay outputs; which means that you can have up to four timers per meter. The start and stop actions can be triggered from the setup menu or by the function keys and digital input. The meter can be setup to display the off/on timer count down.
There are two modes of operation:
Continuous Timer (Interval) At the start of the timer, the output is off and turns on after the Off Delay elapses. The output remains on for the duration of the On Time. The cycle repeats until the user stops the timer either from the menu or a function key.
One-Shot Timer At the start of the timer the output is off and turns on after the Off Delay elapses. The output remains on for the duration of the On Time. The timer stops and the cycle does not repeat.
A sensor detects the bottle is in place and triggers the digital input to start the timer
The timer output controls the filling pump
The On Time is set according to the time needed to fill the bottle
The connectors’ label, affixed to the meter, shows the location of all connectors available with requested configuration.
Current Loop (4-20 mA) Connections
The following figures show a 4-20 mA current loop connected to the meter. The first figure shows the connection with the backlight disabled and the second shows the connection with the backlight enabled. The meter is powered by the 4-20 mA current loop.
Digital Input Connection
A digital input is standard on the meter. This digital input is connected with a normally open contact across DI+ and DI-, or with an active low signal applied to DI+.
4-20 mA Output Connections
Connections for the 4-20 mA transmitter output are made to the connector terminals labeled MA OUT. The 4-20 mA output must be powered from an external power supply.
Relay connections are made to two four-terminal connectors. Each relay’s C terminal is common only to the normally open (NO) contact of the corresponding relay.
Open Collector Outputs
Open collector output 1 and 2 connections are made to terminals labeled O1+ and O1-, and O2+ and O2-. Connect the alarm or pulse input device as shown below.